Need professional heating and cooling services in Fishkill, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Fishkill, NY.
for Fishkill, NY
Our Reviews by City
KC - Fishkill, NY
Rich - Fishkill, NY
Matt - Fishkill, NY
Mike - Fishkill, NY
Eric Rodriguez did a great job and was very courteous. Management cares about their customers. Pricing needs a little work!
Luisa - Fishkill, NY
Bill - Fishkill, NY
Polite and Professional
Jay - Fishkill, NY
Impressed the way Chris interacted with our dog... who can be a handful.
Great customer service
Jim - Fishkill, NY
Margaret was wonderful. She stated in close contact with us at every step along the way.
Morris - Fishkill, NY
Good clean installation, professional workmanship
Morris - Fishkill, NY
Clean installation and start up
Air conditioner annual service
David - Fishkill, NY
There was a problem. Chris diagnosed what the problem was and ordered the parts we needed.
Justin - Fishkill, NY
Scott was very professional and polite! Thanks Scott for a job well done!
Maryann - Fishkill, NY
Two techs showed up on time and were very helpful and did a thorough job. I am very satisfied with Folkes for both my heating and ac needs. Highly recommend!
Gina - Fishkill, NY
Great and prompt service
William - Fishkill, NY
Aaron - Fishkill, NY
Tony is professional and courteous.
Rosa - Fishkill, NY
Daniel - Fishkill, NY
I had my HVAC system installed in the spring of 2019. I was very happy then and remain so. I signed up for a service contract and they came out twice a year to check my heating on one visit and my A/C on the other. Today was my A/C checkup. As always, professional and thorough!
Valerie - Fishkill, NY
Donald - Fishkill, NY
Folkes service staff consistently provides highly proficient servicing of all our ac/ heating equipment. Also, the office staff are always very polite and professional in all communication. Thanks again.
Professional with a warm edge. Great work and neat job
Elise - Fishkill, NY
I would recommend the team that installed the gas line
Rosemarie - Fishkill, NY
Amazing service and great price!!
Lauren - Fishkill, NY
I’m so pleased with the great service I received today from Shane and two of his coworkers. He was professional, nice, and very competent in his job. I will definitely use this company again!
John - Fishkill, NY
Our old gas boiler unit needed replacement and Folkes was able to come out timely, provide a very reasonable price for a new unit and delivered space heaters so we weren't left out in the cold. The technicians that came to install the unit were very professional and provided excellent service. I would highly recommend Folkes for any heating service/installation!
Donald - Fishkill, NY
Clear and precise
Ac tune up on new install. Took pressures, checked capacitor, blower motor, contactor, fan and compressor. Cleared drain line. Took temperatures. Customer stated air was coming from evaporator coil cover, sealed cover with foil tape, also went over spots on supply and return plenum where tape was coming off and customer attempted to use duct tape as a quick fix, re taped with foil tape. System is operating normally.
Found water heater leaking from inside cabinet, insulation soaked at bottom of water heater, we installed water heater four years ago, hard weather is visible on unit and crackling noise on water heater, customer does have a water softener, took deposit for hot water heater and explained warrant process for how water heater to customer.
Ac tune up. Replaced filter, cleared drain, checked blower, coil, took pressures. System running normally. Customer is interested in UV/electronic filter. He will call office when he decides which option he will choose.
Arrived at home for ac tune up. Customer stated outdoor unit was not coming on and a humming sound. Found contactor completely burnt up. Replaced contactor, after replacing contactor only condenser fan would start up, compressor would not kick on. Tested capacitor and capacitor was reading in normal range. Attempted a hard start kit and units compressor would still not kick on. Pressures on low and high side were both at 73. System is r22 and from 1988, customer will have to replace unit. Will schedule comfort advisor appointment for customer.
Arrived at customers home to disconnect the gas line from the grill , Loweâ€™s send the wrong gill to customer,,
Customer downstairs toilet flapper was bad and made toilet constantly run. Simply replaced flapper and adjusted fill valve and toilet was no longer constantly running.
Performed annual AC tuneup. Replaced air filter. Tested unit. System operational.
Ac tune up. New install. Took pressures, checked capacitors, contactor, cleared drain, took temperatures.
Replaced aquastat and tested the system.
Ac tune up. Checked pressures, contactor, capacitors, compressor, fan, blower motor, cleared drain, took temperatures, replaced filter. System running normally. Customer took out Ma for ac and gas.
Completed annual maintenance on air conditioning system. Changed return filter 14x30x1, cleaned indoor coil, tested blower motor capacitor, went to clear condensate trap and noticed trap had a big crack, replaced trap, all wiring looks good, took a delta T reading and had a 20 degree difference, at condenser tested pressures which were normal, tested capacitor which tested low rated for 45UF, reading at 35UF, contactor and out door coil in good shape, system operational and working.
Customer has a leak in water heater. Needs to be replaced. Customer put deposit of half for new tank and remaining balance after job is complete.
No heat or hot water. Customers LWCO light on hyrdrostat IC is red and will not allow boiler to fire up. Pressure is at 15. Boiler was running earlier this morning when light went off but now light is back on and boiler will not fire. Attempted to readjust well sensor and light for lwco was still displayed on hyrdrostat. Read manual for hyrdrostat and there is no way to shut down LWCO. Customer did state that the town did flush his street and he was having brownish water come from faucets for a few days. We will return tomorrow to replace hydrostat and sensor.
Ac tune up. Checked pressures, contactor, capacitor, compress, fan. Cleared drain, checked coil, took temperatures, replaced Merv 11 filter with a customer supplied filter. All readings are normal. System is running normally.
Performed annual AC tuneup. Advise customer R22 system seemed a little low on charge, gave her option to charge unit. Or option for a free estimate on a replacement. Customer will call back if any issues occur
Ac tune up. Replaced filters. Cleared trap and drain, took temperatures, checked evaporator coil, blower motor and capacitor. Took pressures, tested contactor and capacitor. Replaced condenser capacitor. Informed customer that system is old and in rough shape and is R22, recommended to start planning about residential replacement. System is currently running.
Installed Amana 13 seer 3 ton ac condenser with 3 ton First Co. hyrdronic heat air handler. New drain pan with float switch. Merv 11 filter, new return plenum, condensate trap and drain plumbing as needed. New ac pad, linehide, lineset, and low voltage wiring. New switch and gfi at air handler. Installed plywood in attic.
Toilet leaks from the water thank , gaskets and screws between toilet water tank and toilet seat need to be replace , I install a tank to bowl gasket and hardware kit ,check for any leaks,and was working ok
Customer installed ecobee thermostat. Wire has broken off inside push connector. Wire wonâ€™t come out. Checked wiring for thermostat, o.k.. Customer wants to return thermostat and get himself a new one, will wire himself. Recommended hydro air handler/condenser replacement due to age and condition.
I arrived to customer home to diagnose a lose toilet, the toilet was lose and the flange was rotten completely, I explain to the customer that the flange needed to be replace , customer agreed so I proceed to remove and install the repair flange,add wax donut and reinstall the toilet in place
Came to customers home to find thermostat with blank display, changed batteries and display came back tested system turned on and off. Also customer was having a issue with hi shower with water just staying hot and canâ€™t adjuste temperature possible mixing valve issue will need to send plumber to take a look.
Arrived at customers home to test water. Customer has hard water and I recommended that they install a water softener to help reduce the hardness of the water to better protect their pipes and fixtures.
I arrive to diagnose a leak in bathroom sink , I found two different leaks one in faucet steams and the second one is under sink in the main faucet assembly, customer wants to wait until she gets her own bathroom sink and faucet, she know that I didnâ€™t perform any job and water will still be leaking until she gets the new one she will call back to install it when she gets the new one.
Arrived at customers home to replace insulation that had been damaged from a water leak. Ripped old insulation out and padded bay with new insulation.
Estimate to conect a gas line to outdoor drill the was provided by the customer ,reconnected the gas line to the new grill and Check leaks . Customer saw that the grill was working .