Need professional heating and cooling services in Holmes, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Holmes, NY.
for Holmes, NY
Our Reviews by City
Tarra - Holmes, NY
Our old A/C unit was not working. Folkes sent out a technician the next day. He was professional and explained everything. Unfortunately it was not able to be fixed and they sent someone to give us an estimate. He was wonderful at explaining the process, what we needed and what our options were. We ended up replacing our system and the technicians at Folkes were courteous and professional. They put in long hours to get the job done and made sure they kept the the areas they had to walk through and work clean. I would definitely recommend them!
Help - Holmes, NY
After some debate about an anode today that did not exist in our indirect water heater, we used bleach to hopefully kill the bacteria that is causing the sulfur odor in the hot water. Wishing it will be gone with the wind.
Matthew - Holmes, NY
Matthew - Holmes, NY
Technician was very knowledgeable and experienced with the service being provided also very friendly and easy to talk with
Michele - Holmes, NY
Kurt & Chris are the BEST ! Kurt explained everything to me and worked with Chris to fix my furnace. When you call for service ask for them !
Great, fast service, reasonable price
Nicole - Holmes, NY
After calling our usual company about a loud rumbling from our furnace, and being put off until Tuesday, I decided to take advice and give Folkes a try - I’m so glad I did, and so grateful for the fast, efficient service. We signed up for the service plan, a part will be ordered and replaced next week, and the furnace seems to be running much better in the meantime with no noise and no more smell (our furnace is old and Italian - a great furnace but uncommon and nobody keeps parts on hand). I was so grateful for the rapid response, they were here ahead of the promised time, and they couldn’t have been nicer or more professional. It was a great experience, the price was reasonable, and I really couldn’t be happier. Thank you Folkes!
Response from Folkes Heating, Cooling and Burner Service:
Thank you so much for your kind words. Customers like you are the reason we try so hard to provide WOW Service. We appreciate you.
Courteous and competent!
Tina - Holmes, NY
I highly recommend them for your heating and cooling needs!
Performed ac tune up on two systems, checked all components, cleaned coils, checked pressures, temperatures and filters. The filters are cleanable air filters which were clean at this time. The second floor had a clogged drain that was blown out and tested. Recommended duct cleaning on both systems.
System was off upon arrival, found system low on Freon, checked all vents and filters at upstairs unit to make sure of no restrictions. Outside coil clean, thermostat set to 61 in house explained to customer about staging down temperature put thermostat to 70 and recharged system. Tested system and operational.
Installed first co air handler with Amana condenser, new lineset, 20x20 media filter, condensate pump, 2 Honeywell T6 thermostats, new ewc zone panel. New base plenum, reconnected heating pipes, and wiring. Attic unit installed by Matt B/ Mikey, first co air handler, Amana condenser, flushed line set, 20x20 media filter, reconnected heating pipes, new thermostats, new zone panel, secondary drain pan with float switch. Started heat for 2 systems and ac for basement unit.
Found the nozzle strainer clogged and also the head clogged, replaced nozzle and tested.
Call work number first at dispatch. Looking for central air and a heat pump. Does not currently have central air. Oil system. Single family home raised ranch
Customers condense would not start up. Before arriving customer stated they removed mice and a mouse nest from inside condenser. Was not getting 24 volts at the condenser and was getting 24 at air handler. Checked float switch, which was working. Checked wires running in attic no cuts or breaks. Checked wires running into exterior wall no cuts or breaks. Customer stated bathroom was renovated on 2nd floor last year could possibly be issue. Gave customer price for contactor and to run new wire from attic to condenser. Customer stated she would rather replace unit then to invest a significant amount of money into it. She would like to schedule comfort adviser. System is not operational.
Performed oil cleaning. Replaced filter strainer and nozzle, cleaned chamber and flu. Checked expansion tank, aquastat, water feeder, relief valve, Flo controls, circulators, air vent. System operating normally.
Arrived at customers home for complaint of sulfur smell in hot water. Tested water found very slight trace of sulfur. Flush hot water heater with bleach from whole house filter housing and flushed out lines. Recommended to customer he add a mixing valve above hot water heater so he can run the heater at 140 as manufacture recommends for a smell of sulfur but can drop it back down to 120 with mixing valve for safety.
Found system for apartment over garage empty of refrigerant. 20 year old R22 system. Recommended replacement. Customer also has another system for main house that needs replacement. Replacement estimate scheduled for June 16th.
Found blower spinning extremely low RPM causing coil to freeze up and causing suction pressure to be low. Replaced motor checked system running and temperatures. System running and operational.
Performed annual maintenance on air conditioning system. Inside noticed some mold build up on blower wheel and wires which I showed customer will think about possibly doing a UV light. Outside condenser noticed refrigeration levels very low will reschedule to do a leak test.
Clean and service Oil
Completed annual maintenance on 2 ac systems. Cleared drains and traps. Cleaned coils. Didnâ€™t take pressures due to temp. Recommend us light in basement unit. Recommend replacement of both ac systems as per r22. Recommend blower motor cleaning.
Checked operation of oil boiler. Took combustion and efficiency test. All readings normal, 0% smoke. Opened boiler, no soot on sections. Boiler still very clean. There is some soot failing down flue onto boiler. Chimney needs to be cleaned after major sooted boiler cleaning.
Replaced igniter/flame sensor assembly. Started system and checked operation. Cycled on /off serval times and checked ignition and flame sensing capabilities. No problems found at this time.
Spoke to navien and they are sending the flame rod assembly under warranty to be replaced and if problem returns need to check polarity in system
Customer said he got error 004 spoke to tech support and they said it not a very common error code we checked gas pressures ,gas valve ,ground wire to panel,igniter flame sensor adjusted sensor all looked good at this time if problem returns need to walk with igniter
Will receive warranty refund of $2,665.00 once processed and approved, approx 3-5 weeks. RGA# U0202274124
Cleaned and serviced oil boiler, replaced the filter, strainer and nozzle. Brushed and vacuumed inside of the boiler. Everything is operating properly at this time.
Found collector box with two holes so boiler would suck itâ€™s exaust need to call navien to see what is the next step moving forward need to replace boiler
Cleaned and serviced oil boiler, replaced the filter strainer and nozzle. Customer stated the heat would not come on upstairs sometimes and would have to turn the unit off then on again. Found a blower capacitor that was very weak and replaced it. lol her components 8 the attic are working properly. The weak capacitor may not have been starting the blower every time. Also replaced burnt electrodes.
Found boiler not turning on due to loose wire at aquastat repaired and found zone valve for first floor sticking replaced and tested
No heat due to clogged nozzle, replaced, also found oil lines closed due to threaded rings on valves falling off, replaced, system needs maintenance, system operational. Need to call and collect remaining balance of $31.53, approved by DJ
Found oil leak from high pressure nozzle line at oil pump. Took burner apart and dried out oil. Repaired connection and ran burner through several cycles. Did not see any other leaks. Also checked operation of second floor zone valve. Operating normally at this time.
Found oil pump leaking from the seal