Call Folkes Home Services, Cooling & Burner Service at (845) 896-HEAT (4328) for all of your home’s heating and cooling needs in Wappingers Falls, NY. You can rely on Folkes for fast and accurate work performed by experienced HVAC professionals.
Read the reviews below to see why our customers are continually satisfied with our work in Wappingers Falls, NY.
for Wappingers Falls, NY
Our Reviews by City
Service Gas Furnace
Kathy - Wappingers Falls, NY
Easy scheduling, technicians on schedule, polite, efficient. Pricing competitive.
Did a great job.
John - Wappingers Falls, NY
Great Service, Friendly, and very thourough
Jess - Wappingers Falls, NY
Judith - Wappingers Falls, NY
Chris, the technician, arrived promptly, was extremely knowledgeable and friendly. We are very pleased with the service received and highly recommend Folkes for any HVAC service. In addition, they have fair pricing compared to other HVAC service companies.
Great customer service
Kelly - Wappingers Falls, NY
I was kept apprised of arrival time; technician was polite, friendly, and explained everything thoroughly. The only thing I was not happy about was the diagnostic fee; I feel that should be waived if customer decides to have repair done. All other companies I deal with for home repairs do free estimates or waive fee after repair.
On time service great Tech
Rob - Wappingers Falls, NY
The Tech was on time and excellent at the tune up
Mike - Wappingers Falls, NY
I have had Folkes Heating and Cooling for over 6 years. Simply stated: excellent service.
Joe - Wappingers Falls, NY
Chris did a fantastic job!
Ready for winter!
Alice - Wappingers Falls, NY
From scheduling to waving goodbye to the tech, everything was flawless.
Great service. The problem was resolved and we received a good explanation for the work that was done.
Janet - Wappingers Falls, NY
Celina - Wappingers Falls, NY
Service tech was professional and informed me of all work performed and potential issues to be aware of down the road.
Great Professional Service
Rick - Wappingers Falls, NY
I have found Folkes and their technicians to always be courteous, knowledgeable and professional. When I called they sent Noah the same day. He found the problem and did the repair. I was very happy with the work he did. Thanks Rick
Very knowledgeable in my high tech heating system
Sally - Wappingers Falls, NY
Great customer service on time would only want them back again they knew what they were doing and that's what I like
Cleveland - Wappingers Falls, NY
Jay - Wappingers Falls, NY
Prompt and very courteous
Scott/Lidia - Wappingers Falls, NY
Carol - Wappingers Falls, NY
I was very satisfied with the service provided by the technician.
Chris Hait was AMAZING !!!
Vincent - Wappingers Falls, NY
Chris was courteous, knowledgeable, and professional
Professional and well done as always
Ken - Wappingers Falls, NY
Great outfit, we remain very happy with them.
Thorough job. Confident in his work.
Frank - Wappingers Falls, NY
Excellent service and professional and courteous technician
John - Wappingers Falls, NY
We were extremely pleased with the service rendered on Sept. 29, 2020. Our technician, Danny, is first-rate. After inspecting and tuning our gas boiler, he took time out of his busy schedule to walk my property and assess a plumbing job I am considering. Five stars for Danny and Folkes!
Chelsea - Wappingers Falls, NY
Noah did a great job. He was quick, efficient, and helped get our HVAC up and running. This is especially important with our newborn.
Jan - Wappingers Falls, NY
Wappingers falls ny
Charles - Wappingers Falls, NY
Iran was very knowable and polite. He pointed out a problem with a valve and quoted us a price and we are going ahead with the work.
Great diagnosis of problem and great service
Ken - Wappingers Falls, NY
Tyler was excellent. He diagnosed the problem and quickly fixed it. Excellent service! Will request Tyler for next service call.
Cleaned and serviced oil fired system. Replaced filter strainer and nozzle. Checked zone valve, thermostat, circulator, control, primary, transformer, cad cell, expansion tank. System is operating. Noticed air in line, recommended to purge air from pipe.
Replaced blower motor and tested system. System is operational.
Cleaned and serviced two gas systems with MA.
Clean and service oil. Replaced filter strainer nozzle. Combustion test. Checked all components. System operating.
C/S oil and ac. Replaced filter strainer and nozzle, cleaned chamber and heat exchanger. Took pressures. Replaced Merv 11 filter. Customer is interested but would like to wait until spring for duct cleaning and uv system. Both systems operating.
Cleaned and serviced one gas furnace. Cleaned burner box and flame sensor, cleared condensate lines for pressure switch and heat exchanger, added tablets for condensate pump to help break up sludge that customer provided, inspected heat exchanger which everything looked good not rust spots or cracks, all amp readings were normal, tested blower capacitor which was in range, made sure all electrical connections were good, performed combustion test which was normal. System is operational and working. Customer also signed up for one year maintenance agreement
Completed annual tune up on one gas fired boiler. Performed combustion analysis. Cleaned burners. Checked all zone valves. Checked gas pressure. No issues were found at this time.
Completed annual clean and service of one gas fired boiler. Found water all over ground behind boiler. Relief valve was leaking. Expansion tank was full of water and had failed. Found air vent heavily corroded. Also found 2nd floor zone valve heavily corroded and stuck halfway open. Found thermocouple split and cracked. Performed all repairs. Tested operation several times. Supply and returns very hot. Everything is now working properly.
Arrived and found first floor air handler running but the hot water coil was cold. Purged the zone and tested the system, boiler is operating properly. Air vents and water feeder are operating properly. No other issues to report.
Cleaned and serviced gas boiler, checked all components. Replaced a bad expansion tank and air vent. All other components looked okay at this time. After the repairs I tested the system. No other issues to report.
Found code for 292 on the board. States the blower motor has seized bearing or wheel is stuck. The blower is getting power to start but will not start. Submitted a follow up form, customer will need pricing and availability on the part.
Found system not turning on when zone valve was open, it was hitting the end switch but not turning on the boiler. Replaced the zone valve head only and tested system. System is operating properly.
Cleaned and serviced oil boiler, replaced a customer supplied circulator pump, also replaced an air vent and water feeder. Checked all components and tested operation after. System is operating normally.
Found bad damper motor, then shorted aquastat due to the power venter being shorted. Replaced all items and tested the system. System is operating normally.
Clean and service of gas fired heating system. Checked inducer, blower, pressure switches, capacitor, heat exchanger,burners, gas valve, igniter, flame sensor, replaced filter. System operating normally. Recommended uv light and humidifier.
Completed annual clean and service of one gas fired boiler. Removed burners and cleaned. Performed combustion analysis. No issues to report at this time.
Need Sr tech to return.
Found bad primary control, replaced, tested, system operational, checked oil pump, oil burner motor, cad cell eye, electrodes, found parts working fine.
Found bad end switch on zone valve for basement zone. Replaced zone valve for basement tested and cycled system a few times turned on and off every time. Customer signed up for maintenance agreement will call to have it serviced.
Cleaned and serviced oil furnace. Brushed and vacuumed inside heat exchanger and replaced the filter strainer and nozzle.
Cleaned and serviced one gas boiler. Pulled burners and cleaned, vacuumed in burner compartment and around boiler, inspected all water components and controls which look good no leaks, boiler pressure normal, zone valves opened and closed when called upon for heat, measured and adjusted gas pressure was slightly high, took combustion reading which everything looked normal, system operational and working.
Cleaned and serviced two gas furnace with MA. Cleaned and vacuumed burners and burner compartment, inspected heat exchangers which were good, igniter assemblies in good condition, tested capacitors both tested in range, UV light working, all amp readings for blower motor and inducer motor are normal, took combustion readings which all looked normal, reset thermostat back to original temperature. Systems operational and working.
Cleaned and serviced gas boiler, customer would like the calcium flush done on his water heater. We will need to schedule an appointment to get this done.
Cleaned and serviced one gas furnace with MA. Vacuumed inside burner box, inspected igniter assembly which looked good, inspected heat exchanger which looked good, tested blower capacitor, all amp readings of inducer motor and blower motor are normal, customer will change return filters uses a higher Merv rating which they like, both zone motors opened and closed, UV light good, took combustion reading which everything looks normal. System operational and working. Reset thermostat to original temperature.
Put in neutralizer stones in primary trap for Purefire boiler. Cycled boiler and checked drained.