Folkes Home Services, Cooling & Burner Service is proud to offer the residents of Beacon, NY professional heating and cooling services. Our licensed technicians are dedicated to providing you with 5 star service, every time.
Read our reviews below to see how your neighbors in Beacon, NY give us 5 star service ratings. Call us at (845) 896-HEAT (4328) to schedule!
for Beacon, NY
Our Reviews by City
Kiah - Beacon, NY
Danny was punctual and professional. Explained the diagnosis clearly and performed the repair quickly and effectively
Karen - Beacon, NY
David - Beacon, NY
Everybody I talked to was very friendly and communication was clear. Noah Diaz was friendly and seemed to really know what he was doing.
Karen - Beacon, NY
Noah was fast, knowledgeable and patient
On time and thorough. Great.
Thomas - Beacon, NY
Professional and friendly
Christine - Beacon, NY
Awesome customer service
John - Beacon, NY
Very professional from the office to the tech.
Paula - Beacon, NY
Folkes is quintessential excellence
Season check up
Ron - Beacon, NY
Professional and friendly service on Christmas Eve.
Daniel - Beacon, NY
Folkes professionals came promptly on Christmas Eve and fixed kitchen sink, thus making possible our Christmas dinner. Many thanks.
Charles - Beacon, NY
Marguerite - Beacon, NY
Great and prompt service
Tony - Beacon, NY
My appointment was scheduled for between 8 and 10 am. As promised, Scott called upon leaving the office and was at my home by 815. He presented well and had all his needed equipment with him. He performed the contracted service in a timely and thorough manner, then explained his findings to me.
Scott - Beacon, NY
Technician was professional and helpful with my questions and recommendations for service. Recommended additional services based on needs as well as what I didn't need and did not try to "upsell" services just to increase the bill.
Smart guy. Really knows what he is doing!!!
Dorothy - Beacon, NY
Danny was excellent.
Tim - Beacon, NY
Great service and good guy
Eric - Beacon, NY
Really liked Danny. Very friendly and informative.
Maryann - Beacon, NY
I would recommend him highly
Great Service! Technician was thorough, and helpful. Very pleased all around.
Margaret - Beacon, NY
Chris - Beacon, NY
Dan and helper were great. Explained everything clearly. Very thorough. Thx.
Levi - Beacon, NY
Was right on time, kept me informed, was very knowledgeable and professional.
Great team & great service
Tom - Beacon, NY
These folks are professionals. Call for service, get a response immediately. Have a question, they're quick to help. Prices are very competitive but their level of service is far better than the competition.
Great service and no fee
Kristen - Beacon, NY
Appreciated the prompt service and the fee waiver!
Levi - Beacon, NY
Scott was on-time, professional, kept me informed, good service.
Gus - Beacon, NY
Installed new secondary drain pan and hooked up all drainage hoses. Installed new high limit sensor. Had to fix two inch exhaust piping after we lifted unit it was pitched the wrong way, fixed piping and took water out of pipe. Tested system supply vents got up to 130 degrees. System is pretty big for type of duct work, customer may have to increase duct size in future or add temperature sensor in duct work. System operational and working.
Cleaned and serviced gas furnace. Customer stated she had one heating system upon arrival.
Water leaking from general circulator pump at flange, tightened the bolts no more leak, water leak burnt out fan motor inside boiler, replaced, tested, system operational, before operating system had to use heat gun to dry all electrical components in boiler.
Call back, found fan center relay making clicking noise once or twice upon a trial of turning off and on boiler at thermostat 10 times, system is operational, recommend to have part replaced, customer declined and stated they will keep an eye on it.
Customer bought wrong size filter. The filter he bought is 20x20x1 and it should be 16x20x1.
Cleaned and serviced gas boiler. Cleaned burners. Inspected all water components, 3 zone valves,expansion tank, water feeder, air vent, circulater pump, relief valve. Checked wiring. Checked boiler, water, and gas pressure. Performed combustion and efficiency test. Tested unit. System operational
Found unit shooting off an error code of E02, which stated system had five failed attempts to ignite, checked gas valve, gas pressure, all electrical connections, ignitor, found no issues to report, system operational.
Cleaned and serviced gas boiler. Cleaned burners. Inspected ignition system. Checked all water components, 4 zone valves, expansion tank, water feeder, air vent, relief valve, and circulater pump. Checked wiring. Checked boiler, water, and gas pressures. Performed combustion and efficiency test. Tested unit. System operational.
Completed annual clean and service of one gas fired furnace.
Arrived and found leak coming from the attic through a cabinet in the kitchen. Went outside to find the condenser frozen, also the line set frozen. The customer had a t4 pro thermostat on the system now, another friend installed in case the thermostat was bad. I removed the t4 pro and put the t6 pro folkes installed on. Found some settings in the thermostat not set correctly, the was also no cooling mode for it. Went through and reset the thermostat. Tested the heat and A/C, it is working. Could not see any shorts in the wiring that would cause the A/C to come on. The customer is going to leave the breaker for the condenser off in case the tenant leaves for a couple days and something happens again. Need to email invoice
Completed annual maintenance of gas boiler. Customer renewed maintenance agreement for one year.
Cleaned and serviced gas boiler. Brushed and vacuumed burners. Inspected expansion tank, water feeder, air vent, relief valve. Checked gas, water, and boiler pressures. Performed combustion and efficiency test. Tested unit. System operational.
Replaced relay for inducer motor on boiler. Cycled system multiple times with no chattering. Also performed gas cleaning. Removed and cleaned burners, tested inducer, checked all relays, tested gas pressure, checked boiler pressure, expansion tank, air vent, water feeder, zone valves, circulator. System is operating normally.
Cleaned and serviced gas boiler.
Customer was wondering downstairs air flow insufficient felt air flow at vents, system does not have any dampers on collars but found air filter clogged. Customer will get new air filters. On second floor unit system cutting out on high limit, also found unit not condensating properly due to way system is piped for condensation. Fixed piping and so it would condensate. Upstairs unit also has no fresh air pipe connected to unit and attic has spray foam insulation which may be causing issue as well. Will need to order high limit sensor. Customer has heat downstairs and upstairs is pretty warm due to first floor heat rising.
Found thermostat with no display in sanctuary. Replaced thermostat and steam boiler fired up. Watched and tested system everything operational. Pipes very cold will take awhile to heat up no one has been in the church since covid.
C/S Oil. Filter strainer and nozzle. Vacuumed unit. Checked blower, capacitor, igniter, electrodes, and Primary. Vacuumed off washable filter. System is very dusty and full of lint, highly recommend duct cleaning/ blower wheel cleaning, customer does not wish to do either right now, emailed pricing for both duct and blower cleanings, cleanings need to be done. System is operating.
Cleaned and serviced gas boiler. Brushed burners. Checked water components, expansion tank, 3 zone valves, water feeder, air vent, relief valve. Checked wiring. Checked gas, boiler, and water pressure. Performed combustion and efficiency test. Tested unit. System operational.
Arrived and found one zone air bound due to the water feeder being stuck. Freed it and it filled the zone, found the two air vents leaking and the expansion tank bladder bad. Replaced all 3 and purged the system. No other issues to report.
Arrived and customer stated the heat came on in the last hour and went from 59-64. Checked system over and could not find an issue. She will call if it happens again.
Installed 20ft of 1â€ gas line. Pressure tested for 1 hour at 30 psi. Installed Tee where current gas line enters house. Customer wants to be able to extend gas line in the future for a generator.
Found circulator pump not running upon arrival. Boiler temp. At 180 and both zones calling for heat. Pressed on circulator relay and pump turned on. Tightened all high voltage connections for fan center relay and tested pump multiple times. If problem persists recommended to replace fan center relay.
Found system to have a two flash code for pressure switch did not open, first removed trap and cleaned not clogged, pulled exhaust tube to make sure water did not enter inducer fan, cleared all hoses to make sure no blockage. Found pressure switch stuck open put small vacuum to pressure to close it and system fired. Cycled system. System fired every time. Also fixed exhaust tube never glued to rest of PVC causing water leak inside unit.
Replaced Gerber shower stems and trim. Replaced bath sink faucet.
Cleaned and serviced two gas boilers with MA. The first boiler in apt 210 cleaned burners and around boiler, took gas pressure readings which everything looked good, did notice corrosion on air vents gave customer estimate, when doing a combustion test noticed that the ppm were greater than 500, explained to customer I had to shut unit down do no burning efficiently anymore customer is going to need estimate for residential replacement for that boiler. At the second boiler in apt 212 pulled burners and cleaned them and around boiler, took gas pressure readings, noticed boiler pressure at about 20 which expansion tank is n itâ€™s way out gave customer estimate to replace expansion tank and two air vents on this system as well, this boiler burning efficiently. Tested zones and everything operational. Customer renewed maintenance agreement for two gas systems.