Need professional heating and cooling services in Cornwall, NY? Look no further! Folkes Home Services, Cooling & Burner Service provides expert services from highly trained technicians. We work for your comfort and satisfaction.
Check out our customer reviews below to see examples of our high quality work. Choose Folkes as your HVAC specialist in Cornwall, NY.
for Cornwall, NY
Our Reviews by City
Vernon - Cornwall, NY
Scott did a great job. He was professional and knowledgeable as well as being courteous. I would highly recommend him and your service.
Excellent service!! Super friendly service!! More than fair price!!
Alison - Cornwall, NY
Thank you Danny!! You were a blessing at our house this morning!!
Dusty - Cornwall, NY
Technician was prompt and efficient!
Ac tune up. Replaced filter. Customer did not realize she had a 4 inch filter in attic as well as a 1 inch filter in ceiling return. Told customer she should only have one. Customer decided on keeping the one inch filter. After removing the 4 inch and only having one filter my temperature difference went from 15 to 19. Pressures are good. Contactor and capacitor both tested normally. Blower motor amp draw is normal. Cleared trap and condensate line. System is running normally at this time.
Ac x 2. Checked pressures, delta Ts, blower motors, capacitors, cleared drain lines, tested capacitor and contactors. Replaced hard start kit for first floor unit. Both systems operational, both r22 York systems went over phase out with customer. Customer has condensate pump in attic, gave pricing to run new pvc drain. Customer will wait until fall.
Cleaned and serviced one gas boiler with MA. Pulled and cleaned burners and vacuumed inside burner chamber, tested thermocouple which tested very weak and customer had a issue with trying to get it lit the other night, replaced and tested. Tested all zone valves, water feeder was stuck closed freed water feeder, noticed boiler pressure slightly high informed customer that expansion tank may be beginning to fail, left estimate with customer, performed combustion and efficiency test which everything was normal, boiler cut off at temperature. System operational and working.
Re-lite Pilot, tested, system operational.(water heater)
Cleaned and serviced oil boiler, replaced the filter, strainer and nozzle. Also tested system. No issues to report.
Installed and tested part. System is operational.
Need to order part and install on indirect water heater, schedule appointment and give price.
Performed oil cleaning, changed the filter strainer and nozzle. Took a combustion test and checked all components.
Oil line need to be bled, bled, tested, system operational.
845-742-3064 Call George when you arrive, he is the GC Estimate to replace the roof top unit for a three or five sized unit. It is the store that is vacant (old laundromat) between Leo's and Chinese Restaurant.